National Electrical Code Articles and Information
National Electrical Code Top Ten Tips: Article 100 -- Definitions
Based on the 2017 NEC.
Our remarks in are parentheses. Please note, we do quote from
copyrighted material. While the NFPA does allow such quotes, it does so
only for the purposes of education regarding the National Electrical
Code. This article is not a substitute for the NEC.
These are the 10 NEC definitions we deem most important, based on the
pervasiveness of confusion and the potential costs of same. That is not to say other definitions are not also important. Also note that in your particular situation, there may be several definitions more important to you than these. Make a point of learning the NEC definitions, rather than assuming on the fly.
A great way to get up to speed is to set aside "Definition Day" two or three times a week. Keep track of where you left off, each time. What you do is read the first three definitions, slowly. Read them a second time. The next Definition Day, you read those again and add one definition. The next Definition Day, you add one more. From this point forward, you drop the "oldest" definition as you add one more. You will have read all of these definitions several times. By sheer osmosis, most of them will stick.
Now, for our list.
- Ampacity. "The current, in amperes, that a conductor can
carry continuously under the conditions of use without exceeding its
temperature rating." (Ampacity varies depending on many
factors. You must use the appropriate NEC Tables to determine the
- Bonding. The 2017 definition is "Connected to establish electrical continuity and conductivity." I like an earlier definition better, so here it is: "The permanent joining of metallic parts to form an
electrically conductive path that ensures electrical continuity and
the capacity to conduct safely any current likely to be
Bonding is not the same as grounding, but bonding
jumpers are essential components of the bonding system, which is an
essential component of the grounding system. Please note that the
NEC does not authorize the use of the earth as a bonding jumper—that’s
because the resistance of the earth is more than 100,000 times
greater than that of a bonding jumper.
- Continuous Load. "A load where the maximum current is
expected to continue for 3 hours or more." (That is the maximum
running current, exclusive of starting current.)
- Feeder. "All circuit conductors between the service
equipment, the source of a separately derived system, or other power
supply source and the final branch-circuit overcurrent device."
(If there is no branch circuit, a circuit originating at the service
equipment is a feeder. This is a common approach for powering large
- Ground. The 2017 definition is "The earth." Here's an earlier definition: "A conducting connection, whether intentional or
accidental, between an electrical circuit or equipment and the earth
or to some conducting body that serves in place of the earth."
(Please note, simply driving an electrode into the earth does not
constitute grounding a circuit. The ground must be made with respect
to the supply—service entrance or separately derived system—because
electrons are always trying to get back to the source.
- Grounded conductor. "A system or circuit conductor that is
intentionally grounded." (This conductor isn’t meant to serve
as the grounding path. It is simply a conductor that is grounded.
The neutral is grounded on the service side of the service
- Grounding conductor. This term does not appear in the 2017 NEC. Here's the (earlier) definition:
"A conductor used to connect equipment
or the grounded circuit of a wiring system to a grounding electrode
or electrodes." (This is your supply "ground wire,"
not the neutral.)
- Grounding equipment conductor. Actually, equipment grounding conductor (EGC). Here's the 2017 definition: " The conductor path(s) that provides a ground-fault current path and connects normally on-current carrying metal parts of equipment together and to the system gorunded conductor or to the grounding electrode conductor, or both.
Here's an earlier definition: "The conductor used to connect
the non-current-carrying metal parts of equipment, raceways, and
other enclosures to the system grounding conductor, the grounding
electrode conductor, or both, at the service equipment or at the
source of a separately derived system." (Note the difference
between this and the preceding items.)
- Labeled. "Equipment or materials to which has been attached a
label…acceptable to the authority having jurisdiction…."
(It’s important to read the entire original definition, and
distinguish this from "Listed."
- Listed. Equipment, materials, or services included in a list…acceptable
to the acceptable to the authority having jurisdiction…."
(Listing is usually done by an organization like U.L. Most
authorities will not recognize an item as Listed unless it is also
Labeled. Here, too, reading the entire definition is a useful
How the NEC is arranged
- The first four Chapters of the NEC apply to all installations.
- Article 90 precedes Chapter One, and establishes the authority of the NEC.
- Article 80 follows the body of the NEC; it exists as Annex H. It provides the requirements for administration.
- Chapters 5, 6, and 7 are the "special" chapters, covering special: occupancies, equipment, and conditions (in that order).
- Chapter 8 provides the requirements for communications systems.
- Chapter 9 provides tables.
- The appendices provide mostly reference information.
- Appendix D contains examples that every NEC user should study.
Try your NEC moxy:
- Do you know the difference between bonding and grounding? Hint: Look in the NEC, Article 100.
- Does the NEC refer to grounding incorrectly in any of its articles? Yes! So be careful to apply the Article 100 definitions. Don't ground where you should bond.
- When doing motor load calculations, which Article covers hermetic motors? Answer: While Article 440 covers the application of hermetic motors, it does so only by amending Article 430 because hermetic motors are a special case of motors. For motor load calculations, refer to Article 430.
- Does the NEC provide a voltage drop requirement? Yes! It does so in a special case, which is Article 648 Sensitive Electronic Equipment. But for general applications, it does not provide a requirement; it merely provides a recommendation in a couple of FPNs.
- Take our Code Quizzes.
Remember other applicable codes, rules, standards, and references:
- OSHA's electrical worker safety rules.
- IEEE standards.
- NETA standards.
- NFPA standards.
- International Codes (if applicable to the installation).
- State Codes (if the state has them).
- Local ordinances and permit requirements.
- Local fire codes.
- Manufacturer requirements or guidelines.
- Customer security requirements.
- Industry standards.
- Your company's own internal standards, practices, and procedures.
- Engineering drawing notes.
Codebookcity is a subsidiary of Mindconnection, LLC. If you have any questions,
comments, or concerns, please write to sales @ mindconnection.com. We do want