National Electrical Code Articles and Information
National Electrical Code Top Ten Tips:
Article 310 -- Conductors for General Wiring
Based on the 2020 NEC
by Mark Lamendola
Please note, we do quote from copyrighted material. While the NFPA
does allow such quotes, it does so only for the purposes of education
regarding the National Electrical Code. This article is not a substitute
for the NEC.
These are the ten Article 310 items we deem most important, based
on the pervasiveness of confusion and the potential costs of same. Article 310 hugely changed from the 2008 revision (the original writing of this article) to the 2017 revision. The 2020 revision introduced relatively small changes.
Article 310 is arguably the most misunderstood and misapplied area of
the National Electrical Code. The same claim can be made for Article 250
(grounding) and Article 430 (motors). Our intent here is to help clear
up some of the mystery, but a true understanding requires dedicated
study. Do keep in mind ampacity is the amperage capacity of a conductor—the
lower the ampacity, the larger the conductor must be to handle a given
current (though this is in a step fashion, as conductors come in
- What do those conductor jacket letters, such as RHH or THHN mean, and what are the application provisions? You will find the answer in Table 310.4(A). It's a big, multi-page table.
- Conductors must be identified in specific ways, depending upon whether they are grounded [310.6(A)], equipment grounding conductors [310.6(B)], or ungrounded conductors [310.6(C)].
- 310.10 provides an overview of permitted uses. For example, it lists which types of insulated conductors can be used in dry locations and provides yet another list for wet locations. In the 2008 revision, this information was in 310.8. In the 2020 revision, 310.8 is all about marking.
- 310.10(G) provides the requirements for conductors in parallel. The gist of these requirements is that parallel conductors need to be identical: same material, same length, same wire gage, same ampacity adjustments, etc.
- Once place people get confused in the ampacity tables is they don't select the correct temperature column. Read and understand 310.14(A)(3), 310.15(A) and 310.15(B)before attempting to use these tables.
- See and apply Table 310.15(B)(1) and Table 310.15(B)(2) for the ambient temperature correction factors when determining the adequacy of your conductor insulation for the application, before selecting the temperature column when using the ampacity tables.
- Table 310.18 applies to situations where you have three or fewer current-carrying conductors in a single wireway. This is typical for services and feeders, but not very typical for branch circuits. You must select from the column that shows the cable (identified by the insulating material letter designation) you intend to use, and choose between copper and aluminum.
- Table 310.17 and Table 310.19 apply to situations where you have
single-insulated conductors (that doesn’t mean a single conductor—it means the conductor isn’t insulated twice, as would be the case if it’s in an insulated sheath with other conductors) in free air. This is typical for branch circuits. You must select from the column that shows the cable (identified by the insulating material letter designation) you intend to use, and choose between copper and aluminum.
- Table 310.20 applies to conductors on a messenger.
- Table 310.21 provides the allowable ampacities of bare or covered conductors in free air..
How the NEC is arranged
- The first four Chapters of the NEC apply to all installations.
- Article 90 precedes Chapter One, and establishes the authority of the NEC.
- Article 80 follows the body of the NEC; it exists as Annex H. It provides the requirements for administration.
- Chapters 5, 6, and 7 are the "special" chapters, covering special: occupancies, equipment, and conditions (in that order).
- Chapter 8 provides the requirements for communications systems.
- Chapter 9 provides tables.
- The appendices provide mostly reference information.
- Appendix D contains examples that every NEC user should study.
Try your NEC moxy:
- Do you know the difference between bonding and grounding? Hint: Look in the NEC, Article 100.
- Does the NEC refer to grounding incorrectly in any of its articles? Yes! So be careful to apply the Article 100 definitions. Don't ground where you should bond.
- When doing motor load calculations, which Article covers hermetic motors? Answer: While Article 440 covers the application of hermetic motors, it does so only by amending Article 430 because hermetic motors are a special case of motors. For motor load calculations, refer to Article 430.
- Does the NEC provide a voltage drop requirement? Yes! It does so in a special case, which is Article 648 Sensitive Electronic Equipment. But for general applications, it does not provide a requirement; it merely provides a recommendation in a couple of FPNs.
- Take our Code Quizzes.
Remember other applicable codes, rules, standards, and references:
- OSHA's electrical worker safety rules.
- IEEE standards.
- NETA standards.
- NFPA standards.
- International Codes (if applicable to the installation).
- State Codes (if the state has them).
- Local ordinances and permit requirements.
- Local fire codes.
- Manufacturer requirements or guidelines.
- Customer security requirements.
- Industry standards.
- Your company's own internal standards, practices, and procedures.
- Engineering drawing notes.
Codebookcity is a subsidiary of Mindconnection, LLC. If you have any questions,
comments, or concerns, please write to sales @ mindconnection.com. We do want