National Electrical Code Articles and Information
National Electrical Code Top Ten Tips: Article 394 through Article 398 -- Wiring, Miscellaneous
Based on the 2020 NEC
by Mark Lamendola
Please note, we do quote from copyrighted material. While the NFPA
does allow such quotes, it does so only for the purposes of education
regarding the National Electrical Code. This article is not a substitute
for the NEC.
These are the 10 NEC Article 394 through NEC Article 398 items we deem
most important, based on the pervasiveness of confusion and the
potential costs of same.
- NEC Articles 394 through 398 contain the requirements for various
types of wiring, including concealed knob-and-tube wiring, messenger
supported wiring, and open wiring on insulators. Remember that, and your life will be much easier.
- Note that each of these wiring types is a subcategory of wiring in general.
These are very specific wiring methods. The general wiring methods
also apply--but now you have additional requirements if you use any
of these three methods.
- Each Article in this series provides the uses permitted (Section 10) and the
uses not permitted (Section 12.
- NEC Article 394 provides the requirements for concealed
knob-and-tube wiring. While this method is largely disappearing,
there's still an installed base of this type of wiring. You can
install this kind of wiring only to extend or repair an existing
installation. However, if there is open access to the wiring system (e.g., in the attic or in the basement), it may not cost that much or take that much time to replace each circuit with nonmetallic sheathed cable.
- Taps on concealed knob-and-tube wiring must be soldered. Consider replacing the entire circuit with nometallic sheathed cable, so you can install a junction box and use solderless connectors.
- NEC Article 396 provides the requirements for messenger supported
wiring. You must use one of the cable types listed in Table
396.10(A) and follow the appropriate Article for that cable type.
- An exception to the rule just stated applies for industrial
installations [396.10(B)]. This exception does not mean you should necessarily use messenger-supported wiring. The conditions of use might dictate the use of tubing or conduit for increased protection of the cables or conductors.
- NEC Articles 398 provides the requirements for open wiring on
insulators. You won't find open "insulators" defined in
Article 100. So, what does this mean? Look no further than
398.2--this "open wiring on insulators" is a wiring
method. It is not an approach to wiring that involves generic
insulators. Nor does "open" mean "bare".
- If you use the open wiring on insulators method, you must use
bushings to pass the open conductors through framing members [398.17]. And you cannot conceal the circuits [398.12].
- Observe the clearances provided in 398.19.
Codebookcity is a subsidiary of Mindconnection, LLC. If you have any questions,
comments, or concerns, please write to sales @ mindconnection.com. We do want