National Electrical Code Articles and Information
National Electrical Code Top Ten Tips: Article 450 -- Transformers and
by Mark Lamendola
Based on the 2011 NEC
Please note, we do quote from copyrighted material. While the NFPA
does allow such quotes, it does so only for the purposes of education
regarding the National Electrical Code. This article is not a substitute
for the NEC.
These are the 10 NEC Article 450 items we deem most important, based
on the pervasiveness of confusion and the potential costs of same.
- Fuses on the load side don't protect your voltage transformer.
Install overcurrent circuit protection devices (OCPD) on the primary
side of any voltage transformer that is indoors or enclosed
- OCPD sizing for transformers is confusing. Use Table 450.3(A) to
- Autotransformers frequently are installed with improper
overcurrent protection and improper grounding. If installing an
autotransformer, read 450.4 and 450.5 carefully. Do not
install an OCPD in series with the shunt windings.
- 450.5 discusses the grounding of autotransformers. The NEC in
this instance means bonding, not grounding. Review the
definitions of each. If you drive a separate ground rod for an
autotransformer instead of bonding it, you create a difference of
potential and have an unsafe system.
- Tie circuits are another source of confusion and place of error.
Draw these out on paper (or in CAD), so you have a clear idea of
what is going on. Decide where to locate the OCPDs and then review
the design by walking through 450.6, one provision at a time.
- Pay attention to transformer ventilation [450.9]. Many
transformers are installed with their vents facing walls, columns,
corners, or the vents of other transformers (think about how stupid
that is). A transformer in a confined space is also problematic,
ventilation-wise. Consider adding ductwork, flues, or vents to the
confined space so heat doesn't build up. Don't put vents on doors
(doing so exposes personnel to blast hazards).
- If you see a transformer that's "grounded" by a ground rod
driven next to it, you might think it complies with 450.10 but it
doesn't. That's because 450.10 tells you to ground it in accordance
with Article 250. Read through Part V of Article 250. Read the
definitions of grounding and bonding in Article 100. The "ground"
lug on the transformer needs to be bonded in such a way that you
have a path back to the source--not to the earth.
- Not all liquid-filled transformers have the same requirements.
Determine what dielectric fluid you have, then apply 450.23, 450.24,
450.25, or 450.26 as appropriate.
- When configuring the containment aspects of a transformer vault,
doorways and their sills [450.43] become a focal point. The NEC
provides minimal guidance. You must ensure the vault can contain all
transformer fluid in the event of a leak. There are people who
specialize in this kind of thing, so ask if you are not sure. Even
if a transformer isn't in a vault, be thinking in terms of spill
containment while designing the installation.
- A floor drain isn't required unless a vault contains more than
100kVA of transformer capacity [450.46]. But who wants to have
people standing around mopping up transformer fluid and filling
drums with materials that require EPA reports? With a floor drain,
the oil is collected at a central location and disposal requires far
less absorbent material. Discuss the pros and cons thoroughly, if
you are the designer working on a client's project. If you are at
the client end (or doing the work inhouse), consider the impact on
operations if equipment is idled during the cleanup.
Don't take your
electrical exam twice
Journeyman Electrical Exam Prep | Master Electrician Exam Prep
Learn more about:
How the NEC is arranged
- The first four Chapters of the NEC apply to all installations.
- Article 90 precedes Chapter One, and establishes the authority of the NEC.
- Article 80 follows the body of the NEC; it exists as Annex H. It provides the requirements for administration.
- Chapters 5, 6, and 7 are the "special" chapters, covering special: occupancies, equipment, and conditions (in that order).
- Chapter 8 provides the requirements for communications systems.
- Chapter 9 provides tables.
- The appendices provide mostly reference information.
- Appendix D contains examples that every NEC user should study.
Try your NEC moxy:
- Do you know the difference between bonding and grounding? Hint: Look in the NEC, Article 100.
- Does the NEC refer to grounding incorrectly in any of its articles? Yes! So be careful to apply the Article 100 definitions. Don't ground where you should bond.
- When doing motor load calculations, which Article covers hermetic motors? Answer: While Article 440 covers the application of hermetic motors, it does so only by amending Article 430 because hermetic motors are a special case of motors. For motor load calculations, refer to Article 430.
- Does the NEC provide a voltage drop requirement? Yes! It does so in a special case, which is Article 648 Sensitive Electronic Equipment. But for general applications, it does not provide a requirement; it merely provides a recommendation in a couple of FPNs.
- Take our Code Quizzes.
Remember other applicable codes, rules, standards, and references:
- OSHA's electrical worker safety rules.
- IEEE standards.
- NETA standards.
- NFPA standards.
- International Codes (if applicable to the installation).
- State Codes (if the state has them).
- Local ordinances and permit requirements.
- Local fire codes.
- Manufacturer requirements or guidelines.
- Customer security requirements.
- Industry standards.
- Your company's own internal standards, practices, and procedures.
- Engineering drawing notes.